ENGINEERING.com has updated it's forum.  To post a question please visit the new Ask@ Forum.    With a database of over 10000 questions the library will remain available for an extended period.
Q&A

bal
Why the rating of generator is given in KVA & rating of motor is given by KW? View All

16 years ago - 8 months left to answer. - 1 response - Report Abuse
Respond to question
 0 0 0
Responses

phil
All electrical devices that supply power are usually rated in kVA. This includes transformers, UPS's & the like.

Simply put, the difference between kVA & kW is that kVA is "Apparent Power", which does not take into account the Power Factor & kW is "True Power" . See the below equations:

VA = E x I
W = E x I x Cos phi

The above equations are only for single phase.

When a manufacturer makes a transformer, generator, UPS etc, they have no idea of the type of load that will be used & consequently can only rate the device according to its maximum current output that the conductors can safely carry (at untiy Power Factor) & the insulation rating of the conductors (voltage & temperature).

Example.
A single phase transformer capable of delivering 100 Amps at 500 volts would be rated at 50 kVA:
500 x 100 = 50 000 VA (or 50 kVA).

If the Power Factor of any given load was 0.5, the "True" power output of the transformer would be 25 kW:
500 x 100 x 0.5 = 25 000 W (or 25 kW).

16 years ago

Source:

 1 0

ENGINEERING.com does not provide engineering advice. The Ask@ service is a forum for members to exchange ideas relating to the world of engineering. We caution users not to accept any responses that they receive without further validation, and not to rely on any engineering advice that they may get from other members of the Ask@ forum. ENGINEERING.com specifically disclaims any obligation to validate or verify any information posted within the Ask@ service. ENGINEERING.com encourages users to seek the services of a professional engineer for any engineering advice they may require.